<!DOCTYPE html>
<html lang="zh">
<head>
	<meta charset="UTF-8" />
	<meta name="viewport" content="width=device-width, initial-scale=1.0" />
	<meta http-equiv="X-UA-Compatible" content="ie=edge" />
	<title>隐患排查</title>
	<link rel="stylesheet" href="/css/style.css">
	<script src="/js/jquery-2.1.4.min.js"></script>
	<script src="/js/laydate.js"></script>
</head>
<style type="text/css">
	#weiguineir,.chuna,#chrye{
	}
	.prd{
		overflow: hidden;
		white-space: nowrap;
		text-overflow: ellipsis;
	}
	.push_button{
		background: #ededed;
		background-image: -webkit-linear-gradient(top, #ededed, #bab1ba);
		background-image: -moz-linear-gradient(top, #ededed, #bab1ba);
		background-image: -ms-linear-gradient(top, #ededed, #bab1ba);
		background-image: -o-linear-gradient(top, #ededed, #bab1ba);
		background-image: linear-gradient(to bottom, #ededed, #bab1ba);
		-webkit-border-radius: 15;
		-moz-border-radius: 15;
		border-radius: 15px;
		text-shadow: 0px 1px 0px #e1e2ed;
		-webkit-box-shadow: 3px 4px 0px 0px #899599;
		-moz-box-shadow: 3px 4px 0px 0px #899599;
		box-shadow: 3px 4px 0px 0px #899599;
		font-family: Arial;
		color: #3a8a9e;
		font-size: 16px;
		padding: 12px 30px 12px 30px;
		border: solid #d6bcd6 1px;
		text-decoration: none;
		margin: 15px;
	}
	.heading{
		margin: 5px;
	}
	.push_button:hover {
		color: #3a8a9e;
		background: #bab1ba;
		text-decoration: none;
	}
	.ha{
		width:100%;
	}
	.chryec,.dcontent{
		display: none;
	}
	.rtuir{
		display: block !important;
	}
	.divItem .fire{box-shadow: 0 0 0px #AAA;
		padding: 0;
		margin: 10px 0 0px 1%;}
	.goodtxt .fire{box-shadow: 0 0 0px #AAA;
		padding: 0;
		margin: 10px 0 0px 1%;}
	.divItem h2.fire{
		color: red;
	}
	.goodtxt h2.fire{
		color: red;
	}
</style>
<body style="background: #F2F2F2;">
<form action="/ninecheckself/create" method="post">
	{{ csrf_field() }}
	<input type="hidden" name="groupId" value="{{$groupId}}">
	<ul class="noaccordww">
		<?php $i=1; ?>
		@foreach ($entrys as $entry)
			<li>
				<div><span>{{$i}} {{$entry->entry}}</span>
				</div>
				<input type="hidden" name="entryId[{{$i}}]" value="{{$entry->id}}" class="inputIDs">
				<input type="hidden" name="isfire[{{$i}}]" value="0" class="inputIDs">
				<div class="tuijd">
					<img class="yiju" src="/images/yiju.png" alt="">
					<a class="drfa3" href="javascript:void(0)">不涉及</a>
					<a class="drfa2" href="javascript:void(0)" id="ClickMe2">否</a>
					<a class="drfa1 xuanzhong" href="javascript:void(0)" id="ClickMe2">是</a>
					<!--<h1 style="display: none;" class="weigner gieo" style="cursor:pointer">选择隐患</h1>-->
					<input class="chryec-s" type="hidden" name="status[{{$i}}]" value="1">
				</div>
				<div id="dcontent" class="dcontent">
					<p style="display: none;" class="heading">上传文件列表：</p>
					<ul id="files" style="text-align:left;display: none;">
					</ul>
					<div class="turae"></div>
					<input class="chryec" style="margin: 16px 3%;" type="text" name="contentexist[{{$i}}]" placeholder="已查出隐患的定量定性说明">
					<input class="chryec" style="margin: 16px 3%;" type="text" name="content[{{$i}}]" placeholder="未体现的隐患补充">
					<table>
						<tbody>
						<tr class="ha">
							<td><div class="push_button" onclick="appendByCamera()">拍照</div></td>
							<td><div class="push_button" onclick="appendByGallery()">相册</div></td>
							<td><div name="picture[{{$i}}]" class="push_button" onclick="upload(this,{{$i}})">上 传</div>
							</td>
						</tr>
						<input type="hidden" name="picture[{{$i}}]" id="img{{$i}}" value="" />
						<tr class="ha">
						</tr>
						</tbody>
					</table>
				</div>
			</li>
<<<<<<< HEAD
			<?php $i++; ?>
		@endforeach
		<li>
			<input class="chryec-s" type="hidden" name="status[{{$i}}]" value="1">
			<input type="hidden" name="entryId[{{$i}}]" value="0" class="inputIDs">
			<input type="hidden" name="isfire[{{$i}}]" value="0">
			<input type="hidden" name="contentexist[{{$i}}]" value="">

			<div id="dcontent" class="dcontent rtuir">
				<span>其它隐患</span>
				<p style="display: none;" class="heading">上传文件列表：</p>
				<ul id="files" style="text-align:left;display: none;">

				</ul>
				<div class="turae"></div>
				<input class="chryec rtuir" style="margin: 16px 3%;" type="text" name="content[{{$i}}]" placeholder="请填写其它隐患描述">
				<table>
					<tbody>
					<tr class="ha">
						<td><div class="push_button" onclick="appendByCamera()">拍照</div></td>
						<td><div class="push_button" onclick="appendByGallery()">相册</div></td>
						<td><div name="picture[{{$i}}]" class="push_button" onclick="upload(this,{{$i}})">上 传</div>
						</td>
					</tr>
					<input type="hidden" name="picture[{{$i}}]" id="img{{$i}}" value="">
					<tr class="ha">
					</tr>
					</tbody>
				</table>
			</div>
		</li>
		@if($is == 2)
			<?php $i++; ?>
			<li>
				<input class="chryec-s" type="hidden" name="status[{{$i}}]" value="1">
				<input type="hidden" name="entryId[{{$i}}]" value="0" class="inputIDs">
				<input type="hidden" name="contentexist[{{$i}}]" value="">
				<input type="hidden" name="isfire[{{$i}}]" value="1">
				<div class="tuijd" onclick='yiju({{$type}})'>
					<img  src="/images/yiju.png" alt="">
				</div>
				<div id="dcontent" class="dcontent rtuir">
					<span>重大火灾隐患</span>
=======
		<?php $i++; ?>
	@endforeach
	<!--添加-->
	
	
	
	<li>
		<input class="chryec-s" type="hidden" name="status[{{$i}}]" value="1">
		<input type="hidden" name="entryId[{{$i}}]" value="0" class="inputIDs">
		<div id="dcontent" class="dcontent rtuir">
					<span>其它隐患</span>
>>>>>>> 056622f6bbb9773cff9d8d2e7c45ea8a3bb377f0
					<p style="display: none;" class="heading">上传文件列表：</p>
					<ul id="files" style="text-align:left;display: none;">

					</ul>
					<div class="turae"></div>
<<<<<<< HEAD
					<input class="chryec rtuir" style="margin: 16px 3%;" type="text" name="content[{{$i}}]" placeholder="请填写重大火灾隐患描述">
=======
					<input class="chryec rtuir" style="margin: 16px 3%;" type="text" name="content[{{$i}}]" placeholder="请填写其它隐患描述">
>>>>>>> 056622f6bbb9773cff9d8d2e7c45ea8a3bb377f0
					<table>
						<tbody>
						<tr class="ha">
							<td><div class="push_button" onclick="appendByCamera()">拍照</div></td>
							<td><div class="push_button" onclick="appendByGallery()">相册</div></td>
							<td><div name="picture[{{$i}}]" class="push_button" onclick="upload(this,{{$i}})">上 传</div>
							</td>
						</tr>
						<input type="hidden" name="picture[{{$i}}]" id="img{{$i}}" value="">
						<tr class="ha">
						</tr>
						</tbody>
					</table>
				</div>
			</li>
		@endif
	</ul>

	<input type="submit" class="qrtj dibuann" value="下一步">
</form>

<!-- 违规内容弹窗 -->
<div id="goodcover2"></div>
<div id="code22">
	<form id="form1" onsubmit="return false" action="##" method="get" class="goodtxt muc">
		<div class="pItem"
		>
			<p></p>
			<p></p>
			<p></p>
		</div>
		<!--<input onclick="sel()" type="submit" text=""  />-->
		<input id="shezhi" type="submit" text="" />

	</form>
</div>





<!--法律依据开始-->
<!-- 法律法规内容弹窗 -->
<div id="goodcover3"></div>
<div id="code3">
	<form id="form3" onsubmit="return false" action="##" method="get" class="goodtxt muc">
		<div class="divItem">

			<div id="yiju">
				<span style="font-size: 20px;">责任事项及依据</span>
				<!--<h3>1 《安全生产法》第四条</h3>
				<p>生产经营单位必须遵守本法和其它有关安全生产的法律、法规，加强安全生产管理，建立、健全安全生产责任制和安全生产规章制度，改善安全生产条件，推进安全生产标准化建设，提高安全生产水平，确保安全生产。</p>
				<h3>2 《山东省生产经营单位安全生产主体责任规定》第七条</h3>
				<p>生产经营单位应当依据法律、法规、规章和国家、行业或者地方标准，制定涵盖本单位生产经营全过程和全体从业人员的安全生产管理制度和安全操作规程</p>-->
			</div>
			<!--<div id="qingxing">-->
			<!--<h2>追责依据及情形</h2>-->
			<!--<h3>1 《安全生产法》第九十一条</h3>
            <p>生产经营单位必须遵守本法和其它有关安全生产的法律、法规，加强安全生产管理，建立、健全安全生产责任制和安全生产规章制度，改善安全生产条件，推进安全生产标准化建设，提高安全生产水平，确保安全生产。</p>
            <h3>2 《山东省生产经营单位安全生产主体责任规定》第七条</h3>
            <p>生产经营单位应当依据法律、法规、规章和国家、行业或者地方标准，制定涵盖本单位生产经营全过程和全体从业人员的安全生产管理制度和安全操作规程</p>-->
			<!--</div>-->
		</div>
	</form>
</div>
<script>
	$(function() {
		//alert($(window).height());
		$('.yiju').click(function() {
			$("#yiju h3").remove()
			$("#yiju p").remove()
			$.ajax({

				type: "GET",//方法类型weigner
				dataType: "json",//预期服务器返  回的数据类型
				url: "/check/getCheckaccord/"+$(this).parents(".tuijd").siblings(".inputIDs").val(),//url
				data: $('#form3').serialize(),
				success: function (result) {
					$('#code3').center();
					$('#goodcover3').show();
					$('#code3').fadeIn();

					for(var i=0;i<result.checkaccord.length;i++){
						$("#yiju").append("<h3 class='' data-id='"+result.checkaccord[i].id+"'>"+result.checkaccord[i].title+"</h3>")
						$("#yiju").append("<p class='' data-id='"+result.checkaccord[i].id+"'>"+result.checkaccord[i].content+"</p>")
					}
					for(var i=0;i<result.checkcommand.length;i++){
						$("#qingxing").append("<h3 class='' data-id='"+result.checkcommand[i].id+"'>"+result.checkcommand[i].title+"</h3>")
						$("#qingxing").append("<p class='' data-id='"+result.checkcommand[i].id+"'>"+result.checkcommand[i].content+"</p>")
					}



				},
				error : function() {
					alert("数据读取异常！");
				}
			});

		});

		$('#closebt2').click(function() {
			$('#code3').hide();
			$('#goodcover3').hide();
		});
		$('#goodcover3').click(function() {
			$('#code3').hide();
			$('#goodcover3').hide();
			$("#yiju p").remove();
			$("#yiju h2").remove();
		});
		jQuery.fn.center = function(loaded) {
			var obj = this;
			body_width = parseInt($(window).width());
			body_height = parseInt($(window).height());
			block_width = parseInt(obj.width());
			block_height = parseInt(obj.height());

			left_position = parseInt((body_width / 2) - (block_width / 2) + $(window).scrollLeft());
			if (body_width < block_width) {
				left_position = 0 + $(window).scrollLeft();
			};

			top_position = parseInt((body_height / 2) - (block_height / 2) + $(window).scrollTop());
			if (body_height < block_height) {
				top_position = 0 + $(window).scrollTop();
			};

			if (!loaded) {

				obj.css({
					// 'position': 'absolute'
					'position': 'fixed'
				});
				obj.css({
					'top': ($(window).height() - $('#code3').height()) * 0.5,
					'left': left_position
				});
				$(window).bind('resize', function() {
					obj.center(!loaded);
				});
				$(window).bind('scroll', function() {
					obj.center(!loaded);
				});

			} else {
				obj.stop();
				obj.css({
					// 'position': 'absolute'
					'position': 'fixed'
				});
				obj.animate({
					'top': top_position
				}, 200, 'linear');
			}
		}

	})
</script>
<!--法律依据结束-->
<!--提交？-->
<script type="text/javascript">
	function yiju(type) {
		$("#yiju h3").remove()
		$("#yiju p").remove()
		$('#code3').center();
		$('#goodcover3').show();
		$('#code3').fadeIn();
		if (type == 1){//消防
			$("#yiju").append("<h3 class='' data-id='' style='text-align: center;color: red;'>《重大火灾隐患判定方法》（GB35181-2017）</h3>")
			$("#yiju").append("<h2 class='fire'>6 直接判定要素</h2><p class='fire'>6.1 生产、储存和装卸易燃易爆危险品的工厂、仓库和专用车站、码头、储罐区，未设置在城市的边缘或相对独立的安全地带。</p><p class='fire'>6.2 生产、储存和装卸易燃易爆危险品的场所与人员密集场所、居住场所设置在同一建筑物内，或与人员密集场所、居住场所的防火间距小于国家工程建设消防技术标准规定值的75%。</p><p class='fire'>6.3 城市建成区内的加油站、天然气或液化石油气加气站、加油加气合建站的储量达到或超过GB 50156对一级站的规定。</p><p class='fire'>6.4 甲、乙类生产场所和仓库设置在建筑的地下室或半地下室。</p><p class='fire'>6.5 公共娱乐场所、商店、地下人员密集场所的安全出口数量不足或其总净宽度小于国家工程建设消防技术标准规定值的80%。</p><p class='fire'>6.6 旅馆、公共娱乐场所、商店、地下人员密集场所未按国家工程建设消防技术标准的规定设置自动喷水灭火系统或火灾自动报警系统。</p><p class='fire'>6.7 易燃可燃液体、可燃气体储罐（区）未按国家工程建设消防技术标准的规定设置固定灭火、冷却、可燃气体浓度报警、火灾报警设施。</p><p class='fire'>6.8 在人员密集场所违反消防安全规定使用、储存或销售易燃易爆危险品。</p><p class='fire'>6.9 托儿所、幼儿园的儿童用房以及老年人活动场所，所在楼层位置不符合国家工程建设消防技术标准的规定。</p><p class='fire'>6.10 人员密集场所的居住场所采用彩钢夹芯板搭建，且彩钢夹芯板芯材的燃烧性能等级低于GB 8624规定的A级。</p><h2 class='fire'>7 综合判定要素</h2><p class='fire'>a）人员密集场所存在7.3.1-7.3.9和7.5、7.9.3规定的综合判定要素3条以上（含本数，下同）；</p><p class='fire'>b）易燃、易爆危险品场所存在7.1.1-7.1.3、7.4.5和7.4.6规定的综合判定要素3条以上；</p><p class='fire'>c）人员密集场所、易燃易爆危险品场所、重要场所存在第7章规定的任意综合判定要素4条以上；</p><p class='fire'>d）其他场所存在第7章规定的任意综合判定要素6条以上。</p><p class='fire'>5.3.4 发现存在第7章以外的其他违反消防法律法规、不符合消防技术标准的情形，技术论证专家组可视情节轻重，结合5.3.3做出综合判定。</p><h2 class='fire'>7.1 总平面布置</h2><p class='fire'>7.1.1 未按国家工程建设消防技术标准的规定或城市消防规划的要求设置消防车道或消防车道被堵塞、占用。</p><p class='fire'>7.1.2 建筑之间的既有防火间距被占用或小于国家工程建设消防技术标准的规定值的80%，明火和散发火花地点与易燃易爆生产厂房、装置设备之间的防火间距小于国家工程建设消防技术标准的规定值。</p><p class='fire'>7.1.3 在厂房、库房、商场中设置员工宿舍，或是在居住等民用建筑中从事生产、储存、经营等活动，且不符合GA 703的规定。</p><p class='fire'>7.1.4 地下车站的站厅乘客疏散区、站台及疏散通道内设置商业经营活动场所。</p><h2 class='fire'>7.2 防火分隔</h2><p class='fire'>7.2.1 原有防火分区被改变并导致实际防火分区的建筑面积大于国家工程建设消防技术标准规定值的50%。</p><p class='fire'>7.2.2 防火门、防火卷帘等防火分隔设施损坏的数量大于该防火分区相应防火分隔设施总数的50%。</p><p class='fire'>7.2.3 丙、丁、戊类厂房内有火灾或爆炸危险的部位未采取防火分隔等防火防爆技术措施。</p><h2 class='fire'>7.3 安全疏散设施及灭火救援条件</h2><p class='fire'>7.3.1 建筑内的避难走道、避难间、避难层的设置不符合国家工程建设消防技术标准的规定，或避难走道、避难间、避难层被占用。</p><p class='fire'>7.3.2 人员密集场所内疏散楼梯间的设置形式不符合国家工程建设消防技术标准的规定。</p><p class='fire'>7.3.3 除6.5规定外的其他场所或建筑物的安全出口数量或宽度不符合国家工程建设消防技术标准的规定，或既有安全出口被封堵。</p><p class='fire'>7.3.4 按国家工程建设消防技术标准的规定，建筑物应设置独立的安全出口或疏散楼梯而未设置。</p><p class='fire'>7.3.5 商店营业厅内的疏散距离大于国家工程建设消防技术标准规定值的125%。</p><p class='fire'>7.3.6 高层建筑和地下建筑未按国家工程建设消防技术标准的规定设置疏散指示标志、应急照明，或所设置设施的损坏率大于标准规定要求设置数量的30%；其他建筑未按国家工程建设消防技术标准的规定设置疏散指示标志、应急照明，或所设置设施的损坏率大于标准规定要求设置数量的50%。</p><p class='fire'>7.3.7 设有人员密集场所的高层建筑的封闭楼梯间或防烟楼梯间的门的损坏率超过其设置总数的20%，其他建筑的封闭楼梯间或防烟楼梯间的门的损坏率大于其设置总数的50%。</p><p class='fire'>7.3.8 人员密集场所内疏散走道、疏散楼梯间、前室的室内装修材料的燃烧性能不符合GB 50222的规定。</p><p class='fire'>7.3.9 人员密集场所的疏散走道、楼梯间、疏散门或安全出口设置栅栏、卷帘门。</p><p class='fire'>7.3.10 人员密集场所的外窗被封堵或被广告牌等遮挡。</p><p class='fire'>7.3.11 高层建筑的消防车道、救援场地设置不符合要求或被占用，影响火灾扑救。</p><p class='fire'>7.3.12 消防电梯无法正常运行。</p><h2 class='fire'>7.4 消防给水及灭火设施</h2><p class='fire'>7.4.1 未按国家工程建设消防技术标准的规定设置消防水源、储存泡沫液等灭火剂。</p><p class='fire'>7.4.2 未按国家工程建设消防技术标准的规定设置室外消防给水系统，或已设置但不符合标准的规定或不能正常使用。</p><p class='fire'>7.4.3 未按国家工程建设消防技术标准的规定设置室内消火栓系统，或已设置但不符合标准的规定或不能正常使用。</p><p class='fire'>7.4.4 除旅馆、公共娱乐场所、商店、地下人员密集场所外，其他场所未按国家工程建设消防技术标准的规定设置自动喷水灭火系统。</p><p class='fire'>7.4.5 未按国家工程建设消防技术标准的规定设置除自动喷水灭火系统外的其他固定灭火设施。</p><p class='fire'>7.4.6 已设置的自动喷水灭火系统或其他固定灭火设施不能正常使用或运行。</p><h2 class='fire'>7.5 防烟排烟设施</h2><p class='fire'>人员密集场所、高层建筑和地下建筑未按国家工程建设消防技术标准的规定设置防烟、排烟设施，或已设置但不能正常使用或运行。</p><h2 class='fire'>7.6 消防供电</h2><p class='fire'>7.6.1 消防用电设备的供电负荷级别不符合国家工程建设消防技术标准的规定。</p><p class='fire'>7.6.2 消防用电设备未按国家工程建设消防技术标准的规定采用专用的供电回路。</p><p class='fire'>7.6.3 未按国家工程建设消防技术标准的规定设置消防用电设备末端自动切换装置，或已设置但不符合标准的规定或不能正常自动切换。</p><h2 class='fire'>7.7 火灾自动报警系统</h2><p class='fire'>7.7.1 除旅馆、公共娱乐场所、商店、其他地下人员密集场所以外的其他场所未按国家工程建设消防技术标准的规定设置火灾自动报警系统。</p><p class='fire'>7.7.2 火灾自动报警系统不能正常运行。</p><p class='fire'>7.7.3 防烟排烟系统、消防水泵以及其他自动消防设施不能正常联动控制。</p><h2 class='fire'>7.8 消防安全管理</h2><p class='fire'>7.8.1 社会单位未按消防法律法规要求设置专职消防队。</p><p class='fire'>7.8.2 消防控制室操作人员未按GB 25506的规定持证上岗。</p><h2 class='fire'>7.9 其他</h2><p class='fire'>7.9.1 生产、储存场所的建筑耐火等级与其生产、储存物品的火灾危险性类别不相匹配，违反国家工程建设消防技术标准的规定。</p><p class='fire'>7.9.2 生产、储存、装卸和经营易燃易爆危险品的场所或有粉尘爆炸危险场所未按规定设置防爆电气设备和泄压设施，或防爆电气设备和泄压设施失效。</p><p class='fire'>7.9.3 违反国家工程建设消防技术标准的规定使用燃油、燃气设备，或燃油、燃气管道敷设和紧急切断装置不符合标准规定。</p><p class='fire'>7.9.4 违反国家工程建设消防技术标准的规定在可燃材料或可燃构件上直接敷设电气线路或安装电气设备，或采用不符合标准规定的消防配电线缆和其他供配电线缆。</p><p class='fire'>7.9.5 违反国家工程建设消防技术标准的规定在人员密集场所使用易燃、可燃材料装修、装饰。</p>")
		}else{//非消防
			$("#yiju").append("<h3 class='' data-id='' style='text-align: center;color: red;'>《工贸行业重大生产安全事故隐患判定标准（2017版）》（安监总管四〔2017〕129号）</h3>")
			$("#yiju").append("<h2 class='fire'>工贸行业重大事故隐患判定标准</h2><p class='fire'>第一条 为了加强安全生产，坚决防范和遏制重特大事故，指导冶金、有色、建材、机械、轻工、纺织、烟草、商贸行业（以下简称工贸行业）事故隐患排查治理，根据《中华人民共和国安全生产法》等法律法规，制定本判定标准。</p><p class='fire'>第二条 本标准适用于判定工贸行业的重大事故隐患，有关行业领域对重大事故隐患判定标准另有规定的，适用其规定。</p><p class='fire'>第三条 工贸行业重大事故隐患分为专项类重大事故隐患和行业类重大事故隐患，专项类重大事故隐患适用于所有相关的工贸行业，行业类重大事故隐患仅适用于对应的行业。</p><p class='fire'>第四条 专项类重大事故隐患，是指有下列情形之一的： </p><h2 class='fire'>1 存在粉尘爆炸危险的行业领域</h2><p class='fire'>（1）粉尘爆炸危险场所的建（构）筑物为多层厂房时，未设置符合要求的泄爆口的。</p><p class='fire'>（2）粉尘爆炸危险场所设置在居民区内的。</p><p class='fire'>（3）粉尘爆炸危险场所内设置有会议室、更衣室、休息室的。</p><p class='fire'>（4）粉尘爆炸危险场所除尘系统未按工艺分片（分区）独立设置，各除尘系统管网互通互联的。</p><p class='fire'>（5）粉尘爆炸危险场所除尘系统未按照可燃性粉尘爆炸特性采取预防和控制粉尘爆炸措施的。</p><p class='fire'>（6）粉尘爆炸危险场所除尘系统选用干式电除尘器或正压送风除尘的。</p><p class='fire'>（7）粉尘爆炸危险20区、21区域电气设备未使用防爆电气的。</p><p class='fire'>（8）粉尘爆炸危险场所设备设施未采取可靠的防雷、防静电接地措施的。</p><p class='fire'>（9）未制定粉尘清扫制度，对作业现场及设备内部积尘未进行及时规范清理的。</p><p class='fire'>（10）遇湿易自燃的铝、镁等金属粉尘的生产、收集、贮存，未采取防止粉料自燃措施或未配备防水防潮设施的。</p><h2 class='fire'>2 使用液氨制冷的行业领域</h2><p class='fire'>（1）包装间、分割间、产品整理间等人员较多生产场所的空调系统采用氨直接蒸发制冷系统的。</p><p class='fire'>（2）快速冻结装置未设置在单独的作业间内，且作业间内作业人员数量超过9人的。</p><p class='fire'>（3）液氨管线通过有人员办公、休息和居住的建筑物的。</p><p class='fire'>（4）构成重大危险源的储氨单元，未登记建档、定期检测、评估、监控、备案的。</p><h2 class='fire'>3有限空间作业相关的行业领域</h2><p class='fire'>（1）未对有限空间作业场所辨识，并在作业场所设置明显安全警示标志的。</p><p class='fire'>（2）未落实作业审批制度，擅自进入有限空间作业的。</p><p class='fire'>（3）未按照“先通风、再检测、后作业”程序作业的。</p><p class='fire'>第五条 行业类重大事故隐患，是指有下列情形之一的： </p><h2 class='fire'>3.1 冶金行业</h2><p class='fire'>（1）厂内铁水、钢水与液渣，未设专线（或专用通道）运输的。</p><p class='fire'>（2）会议室、活动室、休息室、更衣室等场所设置在铁水、钢水与液渣吊运影响范围内的。</p><p class='fire'>（3）吊运铁水、钢水与液渣起重机不符合冶金铸造起重机的相关要求；炼钢厂吊运铁水、钢水或液渣铸造起重机，未使用固定式龙门钩；龙门钩横梁、耳轴销和吊钩、钢丝绳及其端头固定零件，未进行定期检查，发现问题未及时处理的。</p><p class='fire'>（4）盛装铁水、钢水与液渣的罐（包、盆）等容器耳轴未按国家标准规定要求定期进行探伤检测的。</p><p class='fire'>（5）经大中修或新砌的冶炼、熔炼炉，新砌槽、罐（盆、包）等盛装、运输容器，未按设计要求砌筑、未按设计规定的烘烤曲线烘烤的。</p><p class='fire'>（6）高炉炉基周围，转炉、电炉、精练炉炉下区域，连续铸造漏钢事故可能波及区域，铁合金冶炼出铁、出渣、浇铸区域，铁水罐、钢水罐、渣罐吊运、倒罐等相关作业区域及装载车辆运行区域的地面存在积水，放置有易燃易爆物品的；金属铸造、连铸流程未设置溢流槽、事故罐等高温熔融金属紧急排放和应急储存设施的。</p><p class='fire'>（7）炉、窑、槽、罐类设备本体及附属设施未定期检查，出现严重焊缝开裂、腐蚀、破损、衬砖损坏、壳体发红及明显弯曲变形等未报修或报废，仍继续使用的。</p><p class='fire'>（8）高温工作的熔融金属冶炼炉窑、铸造机、加热炉及相关水冷元件未设置应急冷却水源的。</p><p class='fire'>（9）氧枪、水冷炉壁、炉盖等水冷元件，未配置出水温度与进出水流量差检测、报警装置及温度监测，未与炉体倾动、冶炼电源（电弧炉）、氧气开闭等联锁的。</p><p class='fire'>（10）煤气柜建设在居民稠密区，未远离大型建筑、仓库、通信和交通枢纽等重要设施的；附属设备设施未按防火防爆要求配置防爆型设备的；柜顶未设防雷装置的。</p><p class='fire'>（11）煤气生产、净化（回收）、加压混合、储存、使用等设施附近有人值守的岗位，未设置固定式一氧化碳监测报警装置。</p><p class='fire'>（12）高炉、转炉、加热炉、煤气柜、除尘器等设施的煤气管道未设可靠隔离装置和吹扫设施的。</p><p class='fire'>（13）煤气放散塔的高度低于50米或未点火放散。</p><p class='fire'>（14）休息室、浴室、更衣室设在风口平台和出铁场的下部，操作室、值班室设在热风炉燃烧器、除尘器清灰口等可能泄漏煤气的区域的。</p><p class='fire'>（15）煤气分配主管上支管引接处，未设置可靠的切断装置的；车间内各类燃气管线，未在车间入口设总管切断阀的。</p><p class='fire'>（16）容易聚集窒息性气体的底吹阀门站、室等通风不良场所，未设置通风装置的。</p><h2 class='fire'>3.2 有色行业</h2><p class='fire'>（1）吊运铜水等熔融有色金属及渣的起重机不符合冶金铸造起重机的相关要求。横梁、耳轴销和吊钩、钢丝绳及其端头固定零件，未进行定期检查，发现问题未及时处理的。</p><p class='fire'>（2）装有铜水等熔融有色金属及渣的罐（包、盆）在吊运过程中未走规定线路的。</p><p class='fire'>（3）会议室、活动室、休息室、更衣室等场所设置在铜水等熔融有色金属及渣的吊运影响范围内的。</p><p class='fire'>（4）盛装铜水等熔融有色金属及渣的罐（包、盆）等容器耳轴未定期进行检测的。</p><p class='fire'>（5）铜水等高温熔融有色金属冶炼、熔炼、铸造区域的安全坑内及熔体泄漏、喷溅影响范围内存在非生产性积水的；熔体容易喷溅到的区域，放置有易燃易爆物品的。</p><p class='fire'>（6）铜水等熔融有色金属铸造、浇铸流程未设置紧急排放和应急储存设施的。</p><p class='fire'>（7）高温工作的熔融有色金属冶炼炉窑、铸造机、加热炉及水冷元件未设置应急冷却水源的。</p><p class='fire'>（8）冶炼炉窑的水冷元件未配置温度、进出水流量差检测及报警装置；未有防止冷却水大量进入炉内的安全设施（如：快速切断阀等）的。</p><p class='fire'>（9）炉、窑、槽、罐类设备本体及附属设施未定期检查，出现严重焊缝开裂、腐蚀、破损、衬砖损坏、壳体发红及明显弯曲变形等未报修或报废，仍继续使用的。</p><p class='fire'>（10）经大中修或新砌的冶炼、熔炼炉，新砌槽、罐（盆、包）等熔融有色金属盛装、运输容器，未按设计要求砌筑、未按设计规定的烘烤曲线烘烤的。</p><p class='fire'>（11）有砷化氢气体产生的作业装置未按要求加盖密封，未设抽风装置，现场未配有砷化氢气体检测、报警装置的。</p><p class='fire'>（12）使用煤气（天然气）的烧嘴等燃烧装置，未设置防突然熄火或点火失败的快速切断阀，以切断煤气（天然气）的。</p><h2 class='fire'>3.3 建材行业</h2><p class='fire'>（1）水泥工厂煤磨袋式收尘器（或煤粉仓）未设置温度和一氧化碳监测，或未设置气体灭火装置的；</p><p class='fire'>（2）水泥工厂筒型储存库人工清库作业外包给不具备高空作业工程专业承包资质的承包方且作业前未进行风险分析的； </p><p class='fire'>（3）水泥工厂熟料库等筒型储库结构受力部位，出现裂缝或者钢筋断裂，或基础沉降不均匀，结构主体倾斜严重的；</p><p class='fire'>（4）水泥窑协同处置易燃性固体废物，预处理破碎仓和混合搅拌仓没有配备防火防爆装置的；</p><p class='fire'>（5）玻璃窑炉、玻璃锡槽，水冷、风冷保护系统存在漏水、漏气的；</p><p class='fire'>（6）燃气窑炉未设置燃气低压警报器和快速切断阀，或易燃易爆气体聚集区域未设置监测报警装置的；</p><p class='fire'>（7）纤维制品三相电弧炉、电熔制品电炉，水冷构件泄漏的；</p><p class='fire'>（8）进入筒型储库、磨机、破碎机、篦冷机、各种焙烧窑等有限空间作业时，未采取有效的防止电气设备意外启动、热气涌入等隔离防护措施的。 </p><h2 class='fire'>3.4 机械行业 </h2><p class='fire'>（1）具有可燃性、爆炸危险性及有毒性介质的管道，穿越与其无关的建（构）筑物、生产装置、辅助生产及仓储设施、贮罐区的。</p><p class='fire'>（2）使用、储存易燃易爆物质的设备设施，未采取有效防雷、防静电措施的。</p><p class='fire'>（3）吊运熔融金属的起重机械未选用符合冶金起重机技术条件的铸造起重机，或驱动装置中未设置两套制动器的。</p><p class='fire'>（4）超过20吨的部件吊装，工艺卡或作业指导书中未选定起吊载荷质心的。</p><p class='fire'>（5）铸造熔炼炉前未设置设施防止水流入坑、沟的。</p><p class='fire'>（6）地坑造型时，砂型底部距地下水面的距离少于（1）5米的。</p><p class='fire'>（7）通水冷却的电阻炉未安装水温、水压报警装置的。</p><p class='fire'>（8）保护气氛和可控气氛热处理炉未设置自动切断加热和停止通入生产原料气装置的。</p><p class='fire'>（9）可燃气体加热炉点火前未排除炉内残余的可燃混合气体的。</p><p class='fire'>（10）镁合金轻金属采用盐浴炉热处理时，盐浴温度超过GB 15734最高允许温度限值的。</p><p class='fire'>（11）自动电镀生产线未采取槽液快速循环和溢流措施的。</p><p class='fire'>（12）临时涂装作业未划定作业区域，有机溶剂浓度超过允许限值，作业现场电气设备未采取防爆措施或通风设施配置不全的。</p><p class='fire'>（13）涂装作业中烘干系统的烟囱和焊接作业中的通风烟囱未定期清扫的。</p><p class='fire'>（14）使用易燃易爆的清洗剂（如天拿水）清洗设备或去除油迹时，作业区域有明火或产生火花的作业的。</p><p class='fire'>（15）集聚在地沟、地坑内的易燃易爆气体未及时清除，且周边存有明火作业或高温物体的。</p><p class='fire'>（16）检修作业时无可靠地切断电源、动力源的设施的。</p><h2 class='fire'>3.5 轻工行业</h2><p class='fire'>（1）方便食品制造企业涉及烘制、油炸等高温的设施设备和岗位，未采用必要的防过热自动报警切断和隔热板、墙等保护设施的。</p><p class='fire'>（2）调味品、发酵制品制造企业作为味精生产原料的液氨，其管线通过有人员办公、休息和居住的建筑物的。</p><p class='fire'>（3）食品及饲料添加剂制造企业木糖醇生产加氢环节氢气罐未设防雷接地和静电接地的。</p><p class='fire'>（4）植物油加工企业浸出车间未配备有防爆排风机的。</p><p class='fire'>（5）植物油加工企业浸出车间正己烷储罐的呼吸阀终端和浸出系统废气排出口处未装阻火器的。</p><p class='fire'>（6）白酒储存、勾兑场所未设置乙醇浓度检测报警装置，或浓度报警装置安装位置高于地面0.6米以上的。</p><p class='fire'>（7）储存白酒的金属原酒储罐防雷接地点少于两处的。</p><p class='fire'>（8）原酒输送车未安装防火帽或固定桩未静电接地的。</p><p class='fire'>（9）输酒过程中酒精输入管口未在液面之下的。</p><p class='fire'>（10）木制品加工喷涂车间未设置安全通风装置的。</p><p class='fire'>（11）纸浆制造、造纸企业使用水蒸气或明火直接加热钢瓶汽化液氯的。</p><p class='fire'>（12）日用玻璃、陶瓷、搪瓷制造企业燃气窑炉未设燃气低压警报器和快速切断阀，或一氧化碳聚集区域未设置一氧化碳监测报警装置的。</p><h2 class='fire'>3.6纺织行业</h2><p class='fire'>（1）纱、线、织物加工烧毛、开幅、烘干等热定型设备未按照标准规范设计、安装汽化室、燃气贮罐，或设置在厂房中心位置、多层建筑内的。</p><p class='fire'>（2）燃气贮罐、管道和汽化室未设置建筑防火防爆分隔的，或未设置泄压泄爆、遮挡强光和通风降温等设施设备的；燃气设备、汽化室的本体、阀门、法兰、焊缝等处有腐蚀、泄漏的。</p><p class='fire'>（3）保险粉、双氧水、亚氯酸钠、雕白粉（吊白块）等危险品与禁忌物料混合贮存的，或保险粉未设置专用仓库或露天堆放的。</p><h2 class='fire'>3.7烟草行业</h2><p class='fire'>（1）熏蒸杀虫作业前，未确认无关人员全部撤离仓库，也未设置警戒线和警示标志，且作业人员未配置足够的防毒面具的。</p><p class='fire'>（2）使用液态二氧化碳（干冰）制造膨胀烟丝的生产线和场所，未设置二氧化碳浓度报警仪、煤气（天然气）浓度报警仪、紧急联动排风装置，且未配置足够的空气（氧气）呼吸器的。</p><h2 class='fire'>3.8商贸行业</h2><p class='fire'>（1）进入粮仓进行堆垛或处理结顶作业，未采取有效保护措施的。</p><p class='fire'>第六条 对于不能依据本标准直接判断是否为重大事故隐患的情况，可组织3名以上有关行业领域专家，依据安全生产法律法规、标准规范，进行现场论证、综合判定。</p><h2 class='fire'>第七条 本判定标准自印发之日起施行。</h2>")
		}
	};
	var checkid;
	var checkidde;

	$('#shezhi').click(function sel() {



		var xuanzhongde = $(this).parents("form").children('div').children('p').attr("data-check")
		console.log(xuanzhongde)
		// 提交
		var arr = [];
		var xuanzhong = [];
		for (var i=0;i<$("#form1 .pItem p").length;i++){
			if($("#form1 .pItem p").eq(i).attr("class") == "act"){
				var ids = $("#form1 .pItem p").eq(i).attr("data-id")
				var iue = $("#form1 .pItem p").eq(i).text()
				if(!check) {
					var check = $("#form1 .pItem p").eq(i).attr("data-check")
				}
				arr.push(ids)
				xuanzhong.push(iue)

			}
		}
		console.log(arr)
		$(".noaccordww").append("<input class='e"+check+"' name='negative["+check+"]' value ='"+arr.join(',')+",'  type='hidden' >");
		$('#code22').hide();
		$('#goodcover2').hide();
		checkidde.siblings(".dcontent").children(".turae").children("h1").remove()
		if(checkidde.children("h1.prd")!=""){
			checkidde.children("h1.prd").remove()}

		for (var i=0;i<xuanzhong.length;i++){
			checkidde.siblings(".dcontent").children(".turae").append("<h1 class='weigner prd' data-id='"+1+"'>"+xuanzhong[i]+"</h1>")

		}
	})

	function play() {
		console.log();
		var cont=document.getElementById("ClickMe2");
		console.log('innerHtml cont= '+ cont.innerHTML);
	}
</script>

<script>
	$(function() {
		$("#form1 .pItem").on("click","p",function(){
			if($(this).attr("class") == "act"){
				$(this).removeClass("act")
			}else{
				$(this).addClass("act")
			}
		});
		//alert($(window).height());
		$('.drfa2').click(function() {
//	    	$(this).parents("div").children('h1').siblings().remove()
			checkid = $(this).parents("div").parents('li').children('.inputIDs').val();
//	    	alert(checkid)
			checkidde = $(this).parents("li").children('div').next();
			$.ajax({

				type: "GET",//方法类型weigner
				dataType: "json",//预期服务器返  回的数据类型
				url: "/check/getChecknegative/"+checkid ,//url
				data: $('#form1').serialize(),
				success: function (result) {
					$('#code22').center();
					$('#goodcover2').show();
					$('#code22').fadeIn();
					$("#form1 .pItem").find('p').remove()
					for(var i=0;i<result.length;i++){
						if(i==0){
							$("#form1 .pItem").append("<p class='act' data-check='"+checkid+"' data-id='"+result[i].id+"'>"+result[i].content+"</p>")
						}else{
							$("#form1 .pItem").append("<p data-check='"+checkid+"' data-id='"+result[i].id+"'>"+result[i].content+"</p>")
						}
					}
				},
				error : function() {
					alert("数据读取异常！");
				}
			});

		});
		$('#closebt2').click(function() {
			$('#code22').hide();
			$('#goodcover2').hide();
		});
		$('#goodcover2').click(function() {
			$('#code22').hide();
			$('#goodcover2').hide();
		});
		jQuery.fn.center = function(loaded) {
			var obj = this;
			body_width = parseInt($(window).width());
			body_height = parseInt($(window).height());
			block_width = parseInt(obj.width());
			block_height = parseInt(obj.height());

			left_position = parseInt((body_width / 2) - (block_width / 2) + $(window).scrollLeft());
			if (body_width < block_width) {
				left_position = 0 + $(window).scrollLeft();
			};

			top_position = parseInt((body_height / 2) - (block_height / 2) + $(window).scrollTop());
			if (body_height < block_height) {
				top_position = 0 + $(window).scrollTop();
			};

			if (!loaded) {

				obj.css({
//					 'position': 'absolute'
					'position': 'fixed'
				});
				obj.css({
					'top': ($(window).height() - $('#code22').height()) * 0.5,
					'left': left_position-15
				});
				$(window).bind('resize', function() {
					obj.center(!loaded);
				});
				$(window).bind('scroll', function() {
					obj.center(!loaded);
				});

			} else {
				obj.stop();
				obj.css({
//					 'position': 'absolute'
					'position': 'fixed'
				});
				obj.animate({
					'top': top_position
				}, 200, 'linear');
			}
		}

	})
</script>
<!---->



<script>
	var shanc;
	$(".drfa1").click(
			function raea(){
//			alert(123)
				$(this).addClass("xuanzhong").siblings("a").removeClass("xuanzhong")
				$(this).siblings("input.chryec-s").val(1)

				$(this).siblings("input.chryec").hide()
				$(this).parent().next("div").hide()
				$(this).siblings(".gieo").hide()
				$(this).parent().next("div").children(".chryec").hide()

				shanc = "e"+$(this).parent().siblings(".inputIDs").val()
//			alert(shanc)
				//清空
				$("."+shanc+"").remove()
				$(this).parent().next("div").children(".turae").remove()

			}
	)
	$(".drfa2").click(
			function raea(){
//			alert(123)
				$(this).addClass("xuanzhong").siblings("a").removeClass("xuanzhong")
				$(this).siblings("input.chryec-s").val(2)
				$(this).siblings("input.chryec").show()
				$(this).parent().next("div").show()
				$(this).siblings(".gieo").show()
				$(this).parent().next("div").children(".chryec").show()
			}
	)
	$(".drfa3").click(
			function raea(){
//			alert(123)
				$(this).addClass("xuanzhong").siblings("a").removeClass("xuanzhong")
				$(this).siblings("input.chryec-s").val(3)
				$(this).siblings("input.chryec").hide()
				$(this).parent().next("div").hide()
				$(this).siblings(".gieo").hide()
				$(this).parent().next("div").children(".chryec").hide()
//			清空
				$("."+shanc+"").remove()
				$(this).parent().next("div").children(".turae").remove()

			}
	)
</script>

<script type="text/javascript">
	var server="http://yhpc.ccshe.com/upload/uploadimg";
	var files=[];
	// 上传文件
	function upload(a,b){

		if(files.length<=0){
			plus.nativeUI.alert("没有添加上传文件！");
			return;
		}

		var wt=plus.nativeUI.showWaiting();
		var task=plus.uploader.createUpload(server,
				{method:"POST"},
				function(t,status){ //上传完成
					var rsult=JSON.parse(t.responseText);
					console.log(rsult);
					if(status==200){
						var yu='img'+b;
						var td = a.parentNode;
						var tr = td.parentNode;
						var newImg = document.createElement("img");
						//document.getElementByname('img').value += rsult.data + ',';
						document.getElementById(yu).value += rsult.data + ',';
						newImg.src = rsult.data;

						tr.appendChild(newImg);

						wt.close();
					}else{
						outLine("上传失败："+status);
						wt.close();
					}
				}
		);
		task.addData("client","HelloH5+");
		task.addData("uid",getUid());
		for(var i=0;i<files.length;i++){
			var f=files[i];
			task.addFile(f.path,{key:f.name});
		}
		task.start();
		files=[];
	}
	// 拍照添加文件
	function appendByCamera(){
		plus.camera.getCamera().captureImage(function(p){
			appendFile(p);
		});
	}
	// 从相册添加文件
	function appendByGallery(){
		plus.gallery.pick(function(p){
			appendFile(p);
		});
	}
	// 添加文件
	var index=1;
	function appendFile(p){
		var fe=document.getElementById("files");
		var li=document.createElement("li");
		var n=p.substr(p.lastIndexOf('/')+1);
		li.innerText=n;
		fe.appendChild(li);
		files.push({name:"fileImg",path:p});
		index++;
		empty.style.display="none";
	}
	// 产生一个随机数
	function getUid(){
		return Math.floor(Math.random()*100000000+10000000).toString();
	}
</script>
</body>
</html>